AC 380V 120kA Surge Protector Box With Dual Display Tube
|Place of Origin:||Dongguan China|
|Certification:||CE / ISO9001 / FCC / SGS|
|Model Number:||Power lightning protection box|
Payment & Shipping Terms:
|Minimum Order Quantity:||50 piece / pieces|
|Packaging Details:||Export package|
|Delivery Time:||8 - 15 days after payment|
|Payment Terms:||T/T, L/C|
|Supply Ability:||10000 pieces per month|
|AC:||380V||Protection Level Up:||1.5kV|
|Indication:||Lightning Action Counter And Leakage Current Indication||Product Warranty:||1 Year|
120kA Surge Protector Box,
Dual Display Tube Surge Protector Box,
AC 380V Lightning Protection Box
AC 380V 120kA Surge Lightning Box With Dual Display Tube For Power System
Lightning box120 data:
|Uc(maximum continuous operating voltage)||380V|
|Imax(maximum discharge current)||120kA|
|Up(voltage protection level)||≤2.5kv|
|IP(degree of protection of enclosure)||IP20|
1. Maximum continuous working voltage Uc: 385VAC
2. Nominal discharge current In(8/20μs) : 20kA or 40kA
3. Maximum discharge current Imax (8/20μs):40kA or 80kA
4. Protection level Up:1.8kV or 2.1kV Protection mode: three-phase 4P, single-phase 2P
5. At the same flow capacity, the volume is smaller than the market products;
6. special shell, fire prevention and rust prevention;
7. the remote terminal is firm, and easy to connect;
8. dual display tube indication:Lightning action counter and leakage current indication
How to select SPD?
The first level of power protection:
According to the requirements of national standards: in the main distribution box of the power supply should be installed Ⅰ level test surge protector. The voltage protection level of the surge protector shall be less than or equal to 2.5 kV. The value of the impulse current of each protection mode, Iimp, shall be equal to or greater than 12.5 kA when in uncertainty. Therefore, the lightning protection box of the first stage power supply should choose products with T1 test parameters (10/350μs test waveform), and the impulse current Iimp is ≥12.5kA.
The second level protection of power supply: the second level selection of T2 test (8/20μs test waveform) parameters of the product, the maximum flow capacity (IMAX) : 40kA or 80kA, nominal flow capacity (IN) : 20kA or 40kA can be. Three-phase electric selection of 4P, single-phase electric selection of 2P structure.
The third level protection of power supply:
the third level lightning protection environment is generally single-phase electricity, select T2 test (8/20μs test waveform) parameters of the product, the maximum flow capacity (IMAX) 20kA, nominal flow capacity (IN), the maximum continuous working voltage 275VAC, protection level Up:1.2kA
Scope of application:
Second power lightning protection box is mainly installed in the floor distribution, room distribution and other environments, as the second level of lightning protection of the distribution system, release the remaining surge, with the first level of lightning protection box, to meet the requirements of lightning protection acceptance and protection needs.
Structure and Principle:
Lightning protection box in parallel to the protected equipment front-end, under the condition of normal operating voltage,
power supply lightning protection box in a high impedance state, does not affect the normal work of the circuit. When there is
pulse surge line lightning strike, power lightning protection box in the nanosecond time conduction, quickly put the overvoltage
of diarrhea in the earth, when the pulse over-voltage disappears, power lightning protection box and automatic recovery to a
high resistance state, does not affect the line power supply.
The power distribution system shall adopt a grading configuration according to the standard requirements. The first level protection shall be able to withstand most of the lightning current and pass the T1 lightning shock test. The second level protection shall be configured to discharge the residual lightning current, limit the residual voltage at the equipment end, and cooperate with the first level protection.