Integral Iimp 12.5kA Type 1 Surge Protection Device SPD
|Place of Origin:||Dongguan China|
|Certification:||CE / SGS / ISO9001|
Payment & Shipping Terms:
|Minimum Order Quantity:||200 piece|
|Packaging Details:||export package / Negotiate|
|Delivery Time:||5-15 days after payment|
|Payment Terms:||T/T, L/C, Western Union|
|Supply Ability:||60000 pieces per month|
|CertificationCE,CQC:||CE / CQC / SGS||System Voltage:||220V|
|Environment Temperature:||(-25℃~+60℃)||Status Indicator:||Green(good)/red(need Replacement)|
|Response Time (L-N):||≤100ns||Protection Rating:||IP 20|
|Lightning Protection:||Class 1-4||Colour:||White|
Type 1 Surge Protection Device SPD,
Integral Surge Protection Device SPD,
Iimp 12.5kA SPD Surge Protector
White Type 1 Surge Protection Device SPD Integral Structure Iimp 12.5kA
|Uc(maximum continuous operating voltage)||385V|
|Iimp(impulse discharge current for class I test)||12.5kA|
|In(nominal discharge current for class II test)||25kA|
|Up(voltage protection level)||≤2.0kv|
|Signal deterioration indication||red: replace|
|Housing Material||thermoplastic material|
|Housing self-extinguishing class||UL94_V0|
|Method of connecting wire||multiple|
(Connect In Parallel )
|Mounting method||35mm standard rail installation|
|IP(degree of protection of enclosure)||IP20|
|Remote communication||can add|
|RS485 communication||can add|
Switching type high energy SPD. It is mainly used in the first level lightning protection of power supply system below 400V.
Large discharge energy, fast response time, large flow capacity, residual voltage is lower .
Modular design, lightning protection module is suitable for different power grid system, easy to replace, beautiful appearance.
Imported high energy graphite, stable performance, safe use. No leakage current, no continuation current.
2 years quality guarantee, lifetime free technical support.
Optional communication alarm interface, external RS485 communication interface
set up method
1. The power supply shall be connected with multi-strand copper wires of no less than 6mm2, and the grounding wires shall be multi-strand copper wires of no less than 10mm. The connection line should be as short, straight and thick as possible.
2. The front end of lightning protection device should be connected in series with appropriate surge special circuit breaker(SCB), fuse or circuit breaker.
1, must be disconnected from the power supply when installed, it is strictly prohibited to live operation, the connecting wire must meet the requirements.
2, check the SPD works or not after the lighning protection device installed .
3, lightning protection device no need special maintenance, just regularly check whether the connection is loose, the state indication is normal
accept OEM, can be customized according to customer requirements.